Since 1982, Kevin Shaw Plumbing, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the San Gabriel Valley, East San Fernando Valley and West San Bernadino County. We take special pride in the craftsmen we train and employ--a fact you'll see in their reviews below. Its also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Kevin Shaw Plumbing stands behind the work we do as well as comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Plumbing, Drain Cleaning, AC & Furnace Repair in Altadena, CA. Call us today at (626) 359-1864!
Jose did a great job and communicated very clearly.
Technicians came out to my home right on time. perform the work they suggested, really happy with what was done. thank you Kevin Shaw plumbing
superb pleasant and efficient. took care of the problem
Jose was very quick and provided us great service. He is very nice and friendly and took care of our problem
Our family arose from the bed to find only cold water in the hot water line. Despite surfing through the internet nothing could be found that would remedy the status of our two tank less water heater units. We were not happy about no showers. I got the Kevin Shaw Plumbing number from Angie's List and it was heavenly sent. We had Jose Flores out andstability is a treasure that we hold dear. he analyzed the problem quickly and made recommendations about what to do if it happens again. Jose was totally equipped to fix our problems and was very congenial about his approach. We definitely recommend this business and the pricing was very reasonable. Even when Jose got here and we met him at the door. One could feel the confidence that he would be able to solve our issues with the water heater. We would recommend this company to all our friends and family.
We thought we had a water leak in the ceiling. Jose determined that we had a leak in the ceiling from the recent rains. We only had to pay a basic service fee. When we have a real plumbing problem, I know who to all.
Jose was great in checking out the problem and then giving me a few different options on how I could take care of this situation. The water heater was 10 years old and on the backside of it's life. I chose to replace instead of repair. He did the work right then and there.
Jeff was a great guy, knew his stuff and explained everything while he was working...
Jose Flores did a great job. He came out on time, fixed the problem quickly and it is working great ever since. Thanks. Addi
They replaced my house pipes with copper pipes in one day. The inspector came the next day and approved the work. Then they came back and patched the holes they made in the walls. I got their name from a friend that knew Mr. Shaw
Plumber needed to install earthquake gas valve and washer machine water supply lines as per home owner insurance request after work done tested and found everything working correctly
Plumber needed to snake sewer and use camera equipment. Also attempt repair of Mansfield toilet.
Plumber service call. Found water heater leaking and also a leak from behind the unit.
Plumbing service call. Recommend open wall behind the washer machine. Remove inch and a half drain line for machine. Expose inch and a half to 2 inch drain line. Snake out Internet half drain line behind wall. Next hydrojet with high-pressure washer system to clean and scour drain line. Next reinstall with new 2 inch ABS and fittings to make code correct for wash machine area. Replace existing valves with two new valves for modern style shut off valves at wash machine. Next install new drywall to cover up behind washer machine area. One year warranty if drain line is successfully clean.
Drain Cleaning service. Plumber service. Attempt to clear sewer from clean out. After work done did video and was able to show customer options for maintenance or repair.
Plumber needed to clear sewer line
Heating system needs a new gas assembly valve and new vent to bring to code and make usable. After install of gas control vale found replacement pc board not compatible for unit. Reinstalled original pc board and test. Replace vent pipe in attic. Test system, working fine at this time. Owner is interested in yearly service and check up to keep equipment in good condition.
Cut out section of drive way, dig up bad spot and cut out root growth from sewer. Back fill and patch drive way.
Found parts inside toilet not working. Will have to replace to correct problem. After work done tested and found working correctly. 1 year parts and labor warranty.
Found that toilet water was hot. Turned of water to water heater and looked at toilet again. Toilet was no longer getting water even though cold water was still on. Bathroom is on second floor and water lines are not in attic. Home owner is going to talk to home owners insurance since he just moved in to resolve problem.
Give options for tank type and tankless installation . Owner is looking to remove tank type that is not up to code from existing location. Will let us know after she has gone through all options.
Found sewer backed up. Attempt to snake and camera sewer line. After work done removed a lot of roots. Sewer system has major root problems almost at every joint. Sewer line is about 170 ft. Give pricing to replace sewer line also at a minimum hydrojetting of sewer to buy some time.
Looked at toilet found chain apart. Reattached and found all working correctly.
Found water coming out from planter area next to driveway, recommend removal of bush from area. Found 4" back to back two way clean out system in area. Cable drain line to clear stoppage. After snaking through drain check with video inspection equipment. Sewer line has been relined in the past. Has a dislocated spot in drive way. Need to do spot repair of drive way.
Give pricing to install earthquake gas valve on 3/4 gas system next to home. Also would like us to stub out hot and cold lines from exposed copper lines for laundry. Would like 1/2 inch gas line extended for dryer. Gave pricing for water service replacement to home.
Special Order Shower Valve. Return to repair Altmans custom shower valve. Remove trim and thermostatic mixing cartridge. Install new part and adjust temperature settings on valve, install trim and handle to match temperature output for correct temperature at temperature gage on trim. Next tighten handles on faucet in same bathroom, remove and reinstall cold side lavatory faucet in same bathroom. Safety check water heaters. Also may mention furnaces and spring a/c tune up.
Water repair to attempt a get unit running
Location of leak
Plumber needed drains backed up