Since 1982, Kevin Shaw Plumbing, Inc. is your best choice for repair, installation, and service in homes and buildings just like yours in the San Gabriel Valley, East San Fernando Valley and West San Bernadino County. We take special pride in the craftsmen we train and employ--a fact you'll see in their reviews below. Its also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Kevin Shaw Plumbing stands behind the work we do as well as comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Plumbing, Drain Cleaning, AC & Furnace Repair in West Covina, CA. Call us today at (626) 359-1864!
Jose Flores did a professional job servicing my Rinnai water heater. He answered my questions and generously shared his knowledge about my plumbing issues. I appreciate that he listened and offered a considered assessment. He is a great representative of Kevin Shaw Plumbing.
Polite, prompt and informative... Thank you Kevin
The plumber was very nice.
First called them out for a leaking shower faucet and prices for some other work to be done. The plumber went over all my options with me in detail. I'm a nurse and work odd hours and they worked around my crazy hours. Also go to home home repiped. They even patched up and re-stuccoed all the walls when they were done. Fantastic service. Will definatley use them again!!!
Plumber gave pricing to replace shower valve. Customer under impression originally that it was from work done before. Gave pricing to replace valve and also let her know about financing.
Give pricing for shower valve replacement
Plumbing service call. Plumber found tankless unit in need of service. Unit installed in 2004. Flushed out and cleaned burner assembly. Found that it does not have filtration and needs for proper operation, up to Rinnai specs. Tested after service and found running correctly. Did look at deposits in flushing fluid and found a lot of scale and copper flakes. Indication is that unit may develop a pinhole leak de to hard water.
Plumbing service call. Drain cleaning service call. Found drain system working at this time. Recommend drain service to help with sewer system.
Found drain system working at this time. Recommend drain service to help with sewer system.
Repair to washer lines
Plumber needed to repair pressure regulator
Plumber needed to repair toilet